Plaza By The Park
Existing Non-Residential Building
Green Mark Award for Buildings – Gold
- Estimated energy savings: 1,441,820 kWh/yr; Estimated water savings: 7,600 m3/yr.
- Air-conditioning plant system effi ciency: 0.65 kW/ton
- The chiller system is fitted with Auto Condenser Tube Cleaning System and Variable Speed Drives for all pumps and cooling towers.
- AHUs are fitted with Variable Speed Drives, DDC controllers and CO2 sensors with modulating valve to respond accordingly to load condition.
- Pre-cool AHUs are installed with heat pipes to provide better humidity control by reducing moisture in the air.
Remote Monitoring Service
AHU Fan Replacement
Green Mark Consultancy
Total Building Performance
Solar & Sun Path Analysis
Daylight & Glare Analysis
©2005-2022, G-Energy Global Pte Ltd, All Rights Reserved.